CONCLUSIONS REASONABLY CONSERVATIVE VALUE FOR WET CONCRETE (WITH OR WITHOUT REINFORCEMENT) = 200 Ω-M UNGROUNDED REINFORCEMENT GIVES ABOUT SAME BODY CURRENT AS PLAIN CONCRETE GROUNDING THE REINFORCEMENT IN CONCRETE SUBSTANTIALLY REDUCES BODY CURRENT BASED ON THESE TESTS, STD 80 EQUATION SLIGHTLY UNDERESTIMATES THE EQUIVALENT BODY CIRCUIT RESISTANCE COMPUTATION OF OPEN CIRCUIT VOLTAGE MUST USE MODEL THAT DEPICTS EFFECTS OF GROUNDED REINFORCING MATERIAL – VOLTAGE ON SOIL WILL GROSSLY OVERESTIMATE V touch