[{"text_idx": "#000002", "text": "Comdif CBA is a semicircular perforated displacement diffuser for installation against/on a wall or column. Behind the perforated front plate, CBA is equipped with individually adjustable nozzles, making it possible to alter the geometry of the near zone. The diffuser can be turned and has a circular duct connection (MF measure), so the diffuser can be connected at the top or bottom. The diffuser is suitable for the supply of large volumes of moderately cooled air."}, {"text_idx": "#000003", "text": "The diffuser is suitable for the supply of large volumes of air.\nThe geometry of the near zone can be adjusted using adjustable nozzles.\nDuct covers, plinths and wall brackets can be supplied as accessories."}, {"text_idx": "#000004", "text": "The front plate can be removed from the diffuser, making it possible to clean the nozzles. The visible parts of the diffuser can be wiped with a damp brethyn."}, {"text_idx": "#000005", "text": "Wall bracket: CBAZ \u2013 3 \u2013 size"}, {"text_idx": "#000006", "text": "Can be supplied with duct cover, plinth and bracket for wall mounting."}, {"text_idx": "#000007", "text": "Front plate: 1 mm galvanised steel"}, {"text_idx": "#000008", "text": "The diffuser is available in other colours. Please contact Lindab\u2019s sales department for further information."}, {"text_idx": "#000009", "text": "The near zone is given at an under-temperature of -3 K to a maximum terminal velocity of 0.20 m/s.\nConversion to other terminal velocities \u2013 see table 1, correction of the near zone for -3 K and -6 K respectively"}, {"text_idx": "#000010", "text": "Sound attenuation \u0394L [dB] including end reflection."}, {"text_idx": "#000011", "text": "Table 1 Correction of the near zone (a 0.2, b 0.2 )"}, {"text_idx": "#000013", "text": "Lindab reserves the right to make changes without prior notice"}, {"text_idx": "#000018", "text": "Ni fydd eich cyfeiriad e-bost yn cael ei gyhoeddi. Meysydd gofynnol wedi'u marcio *"}]