text: Gipasimpyohan ang mga Manwal sa Gumagamit.
text: #000000
text: Comdif CBA is a semicircular perforated displacement diffuser for installation against/on a wall or column. Behind the perforated front plate, CBA is equipped with individually adjustable nozzles, making it possible to alter the geometry of the near zone. The diffuser can be turned and has a circular duct connection (MF measure), so the diffuser can be connected at the top or bottom. The diffuser is suitable for the supply of large volumes of moderately cooled air.
text: #000003
text: The diffuser is suitable for the supply of large volumes of air.
  The geometry of the near zone can be adjusted using adjustable nozzles.
  Duct covers, plinths and wall brackets can be supplied as accessories.
text: #000004
text: The front plate can be removed from the diffuser, making it possible to clean the nozzles. The visible parts of the diffuser can be wiped with a damp panapton.
text: #000005
text: Wall bracket: CBAZ – 3 – size
text: #000006
text: Can be supplied with duct cover, plinth and bracket for wall mounting.
text: #000007
text: Front plate: 1 mm galvanised steel
text: #000008
text: The diffuser is available in other colours. Please contact Lindab’s sales department for further information.
text: #000009
text: The near zone is given at an under-temperature of -3 K to a maximum terminal velocity of 0.20 m/s.
  Conversion to other terminal velocities – see table 1, correction of the near zone for -3 K and -6 K respectively
text: #000010
text: Sound attenuation ΔL [dB] including end reflection.
text: #000011
text: Table 1 Correction of the near zone (a 0.2, b 0.2 )
text: #000012
text: Lindab reserves the right to make changes without prior notice
text: #000014
text: Leave sa usa ka comment
text: #000021