Analysis of procedures for heating, ventilation and air conditioning for transfer to low-temperature heat supply
Introduction. Renovation of housing stock supposes construction of new buildings, where the main utilities consuming heat energy will be heating and hot water supply (HWS) systems. Under such conditions the task of heat consumption reduction by transfer to low-temperature and use of the associated procedures is relevant. Materials and Methods. Research was performed on the basis of residential and administration buildings designed within the whole Russia, the facilities were selected based on the year of putting into operation and their purpose. The source of data concerning buildings became documents included into the scope of the design and detailed documentation: plans, drawings and explanatory notes. As meeting the demands of hot water supply makes the main contribution to daily nonuniformities of heat energy consumption, the attention was paid to equipment of hot water supply systems. For calculations, the commercial product of Microsoft Office Excel 2010 was used. Results. During selection of roof boiler house as a source of heat supply increase in consumption of equivalent fuel in relation to the variant of connection to heat power plant operating on solid fuel by 187,314 tons of fuel oil equivalent is possible. General refusal from power-and-heat generation complicates operation of large district heat supply systems. The design parameters of coolant in building heating system differ from project to project: from 95/70 °С, used everywhere till the beginning of the XXI century, up to 90/65 °С corresponding to existing practice of designing or 80/60 °С as at the facility in Sevastopol. Reduction of design temperatures by 5 % is insufficient to decrease general heat consumption of the building. Reduction of heat consumption is explained by selection of advanced materials for pipeline heat insulation. Use of automation diagrams for heat points on the basis of regulator ECL Comfort 310 contributes to improvement of hydraulic control for heating systems, however, concealed automation results in violation of high-quality mode for heat network control and decrease of coolant parameters on adjacent (often non-automated) consumers. Conclusions. Supplement of central high-quality control by local constant temperature/variable flow control at individual heat unit and installation of temperature controllers on heating radiators with mechanical thermostatic head have potential for reduction of the heat energy volume used ineffectively. Increase in level of controllability for heating system together with cheaper and responsive automation systems are basic conditions for increase in quality of heat supply in future.