2、�\行平�,噪音低,�M件同心度高。4、�S封采用���|�C械密封,具有耐磨�p,�o泄漏,使用�勖��L等特�c。消防泵�M代�3。流量Q(L/s)出口�毫�(MPa)�D速n(r/min)功率P(Kw)效率η(%)XBD3.0/5-50(65)50.302900463XBD3.2/5-50(65)0。32竞技游戏竞猜盘口XBD3.4/5-50(65)0。34XBD4.6/5-50(65)50。4629007.558XBD4.8/5-50(65)0.48XBD5.0/5-50(65)0.50XBD7.6/5-50(65)50.7629001550XBD7.8/5-50(65)0.78XBD8.0/5-50(65)0.80XBD11/5-50(65)51。1029003040XBD12/5-50(65)1.20XBD12.5/5-50(65)1.25XBD3。0/10-65(80)100。3029007.571XBD3。2/10-65(80)0。32XBD3。4/10-65(80)0.34XBD4.6/10-65(80)100.4629001567XBD4.8/10-65(80)0。48XBD5.0/10-65(80)0。50竞技游戏竞猜盘口XBD7.6/10-65(80)100.7629002259XBD7.8/10-65(80)0.78XBD8.0/10-65(80)0。80XBD11/10-65(80)101。1029003754XBD12/10-65(80)1。20XBD12.5/10-65(80)1。25XBD3.0/25-80(100)250.3029001576XBD3.2/25-80(100)0。32XBD3。4/25-80(100)0。34XBD4。6/25-80(100)250.4629002274XBD4.8/25-80(100)0.48XBD5.0/25-80(100)0.50XBD7.6/25-80(100)250.7629003769XBD7。8/25-80(100)0。78XBD8.0/25-80(100)0.80XBD11/25-80(100)251.1029007569XBD12/25-80(100)1.20XBD12.5/25-80(100)1。25XBD13/25-80(100)251。3029009057竞技游戏竞猜盘口XBD14/25-80(100)1。40XBD15/25-80(100)1。50XBD3。0/45-100(125)450.3029002273XBD3.2/45-100(125)0。32XBD3。4/45-100(125)0.34XBD4.6/45-100(125)450。4629003777XBD4.8/45-100(125)0.48XBD5.0/45-100(125)0.50XBD7.6/45-100(125)450.7629005580XBD7.8/45-100(125)0.78XBD8。0/45-100(125)0.80XBD11/45-100(125)451.1029009070XBD12/45-100(125)1.20XBD12。5/45-100(125)1.25XBD2.8/55-150(200)550.2814503078XBD3.0/55-150(200)0。30XBD3.2/55-150(200)0。32XBD4.6/55-150(200)550.4614504575XBD4。8/55-150(200)0。48XBD5.0/55-150(200)0.50XBD7。6/55-150550。7629007576XBD7.8/55-1500.78XBD8.0/55-1500.80XBD11/55-150551.10290011073XBD12/55-1501.20竞技游戏竞猜盘口XBD12.5/55-1501.25XBD13/55-150451。30290011080竞技游戏竞猜盘口XBD14/55-1501.40XBD15/55-1501。50XBD4。6/100-2001000.4614507581XBD4.8/100-2000.48XBD5。0/100-2000。50XBD3.0/150-2501500.3014507580XBD3.2/150-2500.32XBD3.4/150-2500.34XBD4。6/140-2501400。4614509072XBD4.8/140-2500.48竞技游戏竞猜盘口XBD5。0/140-2500.50XBD2。4/200-3002000.249707581XBD2.6/200-3000。26XBD2.8/200-3000.28竞技游戏竞猜盘口XBD2.8/200-300(350)2000.2814509084XBD3.0/200-300(350)0。30XBD3.2/200-300(350)0.32XBD4.0/200-3002000.4097013284XBD4.2/200-3000.42XBD4。4/200-3000.44XBD4。6/160-3001600.46145011078XBD4.8/160-3000.48XBD5。0/160-3000.50XBD4.6/200-3502000。46145016083XBD4。8/200-3500.48XBD5.0/200-3500。50XBD2.8/300-4003000.28145013276XBD3。0/300-4000.30竞技游戏竞猜盘口XBD3.2/300-4000。32竞技游戏竞猜盘口XBD2.8/330-5003300.28145016078XBD3.0/330-5000。30竞技游戏竞猜盘口XBD3.2/330-5000。1、不出水a、�M出口�y�T未打�_,�M出管路堵塞,流道�~�堵塞。c、吸入管漏�狻�d、泵�]灌�M液�w,泵腔�扔锌�狻�e、�M口供水不足,吸程�^高,底�y漏水。f、管路阻力�^大,泵�x型不��。a、�z查,去除堵塞物。b、�{整��C方向,�o固��C接�。f、�p少管路��道,重新�x泵。2、水泵流量不足a、先按1.原因�z查。b、管道、泵流道�~�部分堵塞,水垢��e,�y�T�_度不足。