Analysis of Relay Protection Responding to a Transformer Fault
Introduced a typical 220 kV transformer protection operation behavior when the transformer interturn fault and grounding fault occurs.Through analyzing the fault wave graphics and operation behavior of relay protection equipment in detail,solved doubts,demonstrated protection behavior is correct,and finally put forward some advices.