Need some advice please. The TRV's in my 3 bedrooms upstairs come on in even when they are turned off, will they all need to be changed or could it be something else?, also if they need to be changed, is it an easy job to do. many thanks in advance.
Three points. Firstly, older TRV's didn't actually have an off setting. IF you look at the valve and the lowest setting is a * (snowflake) this is a frost setting, and whilst in the summer may pretty well switch off, still may allow a minimal flow if the room is cold. Only valves with a 0 (Zero) setting guarantees an off.
Secondly, as valves age, scale and deposits build up on the seal surface preventing the valve from shutting fully.
Lastly, the head may fail causing the valve to stay open.
All older style TRV's were supplied with a cap that replaced the thermostatic head and allowed the valve to be shut manually. Of course, these are always lost!
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!