Partial Discharge Detection and Defect Location Method in GIS Cable Terminal

The complex structure of gas-insulated switchgear (GIS) cable terminals leads to serious electric field concentration, which is a frequent fault position of a high-voltage cable system. At present, due to the differences in the frequency bands of sensors, various partial discharge detection technologies have certain differences in their scope of application and anti-interference performance, resulting in a low defect detection rate in GIS cable terminals. In this paper, a comprehensive diagnosis scheme is proposed, which integrates transient earth voltage (TEV), ultra-high frequency (UHF), high frequency (HF), and ultrasonic methods. Two abnormal discharge defects of GIS terminals in two 220 kV substations in Tianjin were tracked and monitored, and the joint diagnosis was carried out using the proposed scheme; the type of discharge defect and the phase sequence of the defect were determined, and the UHV was employed to precisely locate and analyze the defect source. Finally, through the disassembly analysis and electric field simulation of the GIS cable terminal, the accuracy and effectiveness of the discharge detection and location method were verified, providing a typical detection demonstration for the defect diagnosis of a GIS cable terminal.